Find great deals for Allen-Bradley OF8C (OF8C) Output Module. Shop with confidence on eBay!. Buy PLC analogue i/omodule,OF8C OF8C. Browse our latest plc-i-o- modules offers. Free Next Day Delivery. : Analog Output Module CompactLogix, 8-ch. single-ended, 0/mA, panel mount ˄TS35, Allen-Bradley, #OF8C, PLCs.
|Country:||Sao Tome and Principe|
|Published (Last):||25 June 2015|
|PDF File Size:||1.22 Mb|
|ePub File Size:||2.84 Mb|
|Price:||Free* [*Free Regsitration Required]|
Somebody help me with configuration parameters. CompactLogix analog modules o8fc to get a power cycle or a reconfiguration command before they will accept a reconfiguration. Find More Posts by rdrast. January 15th, Originally Posted by rdrast. Logic circuits process the signal. An input LED turns on or off indicating the status of the corresponding input device.
Please read this important info!!! Please DON’T use it for advertising, etc. Ab Plc5 Rio Problem.
An output module controls the output signal in the following manner: Optical isolation separates module logic and bus circuits from field power. I recommend downloading your program and cycling power to the controller. March 7th, Please DON’T use it for advertising, etc.
January 15th, If not filtered, voltage transients could produce false data.
Output Module OF8C Configuration – – Interactive Q & A
January 14th, Originally Posted by Ken Roach. You’re right about the clamp values.
Logic circuits determine the output status. Analog Output Module CompactLogix, 8-ch.
See product data sheet from Downloadable files. I always make a point of that when teaching analog output configuration Are you seeing any faults? Find More Posts by Ken Roach. August 9th, Find More Posts by Elcan. Add a suppression device directly across the coil of an inductive device to reduce the effects of voltage transients caused by interrupting the current to that device and to prolong the life lf8c the switch contacts.
Controller SLC 5/05 16K Ethernet & RS-232, Allen-Bradley
April 4th, It solved and I got Have you wrote configuration data over yet? Originally Posted by rdrast Somewhat WAG here, but if you if8c up the properties box on the analog module, and go to limits, do you have the limits set to appropriate values? August 24th, I personally prefer to keep my engineering units as close to physical volts or milliamperes as possible, so if it were my system I would set it up for “Engineering Units”.
The time now is All times are GMT All input modules use input filtering.
Please click here to register!